OUTPUT Control,Alarm or Logic Output. Universal Process Input. 0 to 50 mV Z. 0 to 20 mA Z. 0 to 10 V Z. Pt CAT II. Y c. ESM MODULE – 2. NC. is done with it ‘s selectable ON-OFF, P, PI, PD, PID,. AutoTune and Self Tune PID properties. ESM, ESM ESM, ESM ESM eng esm 02 v04 07_14_ Home; eng esm 02 v04 07_14_ Anterior. eng esm 02 v04 07_14_
|Published (Last):||10 October 2013|
|PDF File Size:||6.23 Mb|
|ePub File Size:||15.76 Mb|
|Price:||Free* [*Free Regsitration Required]|
Be sure to use the rated power supply voltage to protect the unit against damage and to prevent failure. It can be changed according to analogue input type and scale. Value between 5 and seconds can be entered. This parameter is visible if Logic output function of Output-3 is Alarm output and one of the analogue input modules is plugged in Module-1 or Module-2 socket Minimum value of operating scale Low Limit.
This warranty is in force if duty and responsibilities which are determined in warranty document and instruction manual performs by the customer completely. The unit normal to return to work, the device energy cut-off and Analog Input one of the modules must be removed.
Press menu button to exit without saving Set value. It is active if logic output function of Module-1 is an alarm output. If motorized valve control is selected this parameter is active ON The minimum duration of the valve motor drive output 0.
For soak operation ; process value is constant in step set value that are defined in these parameters for time that are defined in soak time parameters. This must be selected if analogue input module ems Module-1 socket is EMI This parameter is visible if one of the analogue input modules is plugged in Module-2 socket Alarm on wsm time 0, Seconds It is active if logic output function of Module-1 is an alarm output Alarm off delay time 0, Seconds Alarm off delay time.
Deviation range alarm Heater failure alarm. Maximum value of operating scale High Limit. During the equipment is ems in hole on the metal panel while mechanical installation some metal burrs can cause injury on hands, you must be careful.
eng esm 02 v04 07_14_ – Disai Automatic Systems
It can be adjusted from 0 to When tune operation finishes, it can be changed by the device. Alarm- 3 hysteresis value. It turns to operation screen without accessing to parameters. Operator can see operator menus and parameters but operator can not change the parameters.
This warranty is provided for a period of two years.
It is active ifV CT input module is plugged in Module-2 socket. It determines logic output function of Output This parameter is visible if one of the analogue input modules is plugged in Module-1 or Module-2 socket Measurement input selection for Output-3 alarm output.
Emko Elektronik Sanayi ve Ticaret A. Defines maximum value for selectable dual point calibration. Selectable dual point calibration is performed. PT input type selection.
After complated the tunning ems, integral time value changes automatically. Cut power to the device before accessing internal parts. This value is added to the process value.
Universal technological PID-controllers of the series ESM-xx50, xx30, xx00
If it is 0, integral control part does not perform. In 450- One piece unit – Twopiece mounting clamp – One piece instruction manual AUTO Maintenance Repairs should only be performed by trained and specialized personnel. Do not use the unit in combustible or explosive gaseous atmospheres.
Even if this parameter is 0, this parameter is accepted 50 msecs for security. It means alarm latching output is selected.
Process high alarm Process low alarm Measured value from analogue input module in Module-1 socket is not used as process set value. Configuration of digital input in Module-1 socket. Use a cloth dampened in ethyl alcohol or water to clean the external plastic case.
ESM-4950 “Smart IO Module” Process Controller
Use of these solvents can reduce the mechanical reliability of the device. Keep the power off until all of the wiring is completed so that electric shock and trouble with the unit can be prevented.
Never attempt to disassemble, modify or repair this unit. General Parameters Minimum value for process set and alarm set values Maximum value for process set and alarm set values 2.
Device does not allow to do any changes without entering the password correctly. Fixed dual point calibration is performed. When tune operation finishes if this parameter is 0, it can not be changed because derivative control part does not perform.
If the mounting clamps are on the unit, put out them before inserting the unit to the panel. Display adjustment low point value is fixed todisplay adjustment high point value is fixed to